Primary Pressure Regulating Valve
What is the difference between a primary pressure regulating valve and a differential pressure regulating valve?
"Primary pressure regulating valve" is installed as a relief valve for the pump in the air conditioning facilities for high-rise buildings adopting the open circuit method. "Differential pressure regulating valve" is installed in the facilities adopting the close circuit method, where a pump needs to run at the stable flow rate regardless of the back pressure. GD-20R primary pressure regulating valve and GD-21 differential pressure regulating valve are the major products in our product lineup.
Which size of mesh is recommended for the strainer applied to a primary pressure regulating valve to prevent foreign substances?
The size of 60 to 80mesh is recommended in the case that the controlled fluid is liquid or gas.
Searches are executed in Product Q&A. Enter keywords to be searched for.
You can enter one or more keywords.
When you enter two or more keywords, put space between them.